Andreas Posted August 30, 2022 Report Share Posted August 30, 2022 Hello, We have a internal discussion about how to calculate DC cables. I have been told that it its 2 way (go and return) including the extra lenght of the connection cables. My colleague thinks it is one way including modules. In PV-Sol there is been written 1x go and return. What length must i put in with a 100mtr from inverter to module to calculate te totall loss. is it (a) 100 + connection cables modules. ±140mtr (b) 100 + connection cables and return ±260mtr Quote Link to comment Share on other sites More sharing options...
Join the conversation
You can post now and register later. If you have an account, sign in now to post with your account.
Note: Your post will require moderator approval before it will be visible.