RicardoM Posted May 7, 2019 Report Share Posted May 7, 2019 Good morning, I am considering the following configuration of 5 strings of 18 modules each with the 20KTL Huawei inverter and AC-300M/60S modules: That is, not the typical configuration of two identical strings per MPP, as the current would be too high: I understand that the first configuration is possible, but I'm not sure how the connection would be done in the "real world". Would it be a string per MPP input entrance, leaving the sixth unused? How would the inverter know I'm not following the second configuration, which is not allowed? Thanks in advance, kind regards, Ricardo Quote Link to comment Share on other sites More sharing options...
Join the conversation
You can post now and register later. If you have an account, sign in now to post with your account.
Note: Your post will require moderator approval before it will be visible.